Active Harmonic Filters Improve Dynamic Test-Bed
A major pioneer in the manufacturing industry caused problems on the power supply network with their dynamic test bed. Here, an installation of the right combination of active harmonic filters now compensates harmonics up to the 100th order with great results. Both harmonics and voltage notches are reduced to enable top performance of the equipment.
The test benches, owned by the development department of a major European production plant, are used to test components in the development phase. Varying test conditions can be programmed, which gives the test bench very dynamic properties.
Harmonics Compensation Challenge
The same transformer is connected to two parts of the test bench. With a very dynamic load whose load current amplitude can change from zero to maximum in approximately 100 МС, it was impossible to run both parts of the test bench simultaneously. The voltage notches of up to 25% in combination with very high harmonic disturbances prevented this. This caused serious delay in the testing facility as well as exceeding the limits in EN61000-2-4.
Активни Хармонични Филтери - Решење
To solve the power quality issues, several active harmonic filters were installed to compensate the disturbances. Two 200/480V filters were installed together with one 100/480V filter that in combination compensate all frequencies up to the 100th harmonic order. The first two filters can be used to compensate lower harmonics while the third compensates for higher order harmonics and interharmonics. The three units were configured to share the
load with the 100/480V filter working on higher orders only. This resulted in extremely short response times and considerably lowered load disturbances.
Harmonics Compensation – the Result
Thanks to the active harmonic filter installation, voltage notches could be reduced to 10%. Додатно, harmonics were lowered to the required level stipulated in EN61000-2-4. Сада, both test benches can be run simultaneously without any of the problems caused by poor power quality.
Извор : Активни Хармонични Филтери